Chinook Power Station is located near Swift Current Saskatchewan, Canada and owned by SASKPower. The power plant is a 350 MW combined cycle power plant utilizing natural gas. SPG supplied the air cooled condenser utilizing its modualaire design – 4 streets by 3 rows with 12 fan units.
Regulations in Saskatchewan are phasing out conventional coal-fired generation and requiring the integration of intermittent renewables and SaskPower, the province’s sole energy provider, sought to provide cleaner energy to the surrounding area.
The power station generates enough electricity to meet the growing demand for power in the area, providing power for at least 350,000 homes. It supports the electric utility’s goal of a 40% reduction in greenhouse gas emissions by 2030, exceeding the national target of a 30% reduction.
Customer initiated contact asking about any experience that Galebreaker had seen with high winds affecting ACC and ACHE performance. This is an extremely windy site and the customer explained that they were experiencing wind speeds of 19m/s (43mph) that were causing two main challenges:
- A host of mechanical performance problems such as fan blade failures
- Thermal performance losses – mass flow rate / vacuum performance
- Wind blown debris from the site entering the ACHE unit and causing fouling
Galebreaker were contracted to do a customised CFD analysis at 19 m/s wind speed. The CFD analysis showed substantial thermal performance benefits and the project went forward. The design offered 10m high cruciform screens using M75, and M60 perimeter screens used for 3 sides of the ACC just beneath the fan deck. The original OEM (SPG) was contracted to do the structural analysis to assess the loads from the wind screens and several straightforward braces were added. Debris protection screens were also provided for their ACHE air coolers which consist of 4 air coolers with 3 cells each. These are designed as full height screens and have a roll up door for each unit. Galebreaker utilized Kipcon to analyze the ACHE structure and analysis showed no reinforcing was required. Materials were delivered in October 2022 and installed in April 2023 in under 3 weeks.
For the ACC performance benefits, the customer is expecting to see a 31% recovery of ACC thermal power, as well as significant improvements to their mechanical challenges. The cruciform wind screens will improve mass flow rate and provide thermal recovery, whilst the perimeter screens will improve dynamic fan blade loading by stopping the effects of wind shear and gusts underneath the fans. The full height screen design for the ACHE air coolers will prevent wind blown debris from fouling the fin tubes.
Check some of our projects to know how we help businesses solve their challenges
Full Weather Protection in Ontario
North Bay Power Plant
Performance Improvement in a Challenging...
Improving ACC Airflow in Massachusetts
The Dighton Power Plant
Installing a cruciform configuration underneath the ACC with our patented M75...
Improving Fan Performance near Las Vegas
Both cruciform and perimeter screens improve performance at the Apex Generating Station...
Improving Mechanical Performance near Boston
Blackstone Energy Project
Reducing fan and gear reducer stress at the ANP Blackstone Energy...
Mega Watt Output Improvement in Mexico
Rio Bravo Energy
Improving vacuum on hot windy days at the Rio Bravo Energy...
Mitigating Wind Effects on ACC and ACHE
Chinook Power Station
Chinook Power Station is located near Swift Current Saskatchewan, Canada and owned by SASKPower. The power plant is a 350 MW combined cycle power plant utilizing natural gas. SPG supplied the air cooled condenser...
Motorized Wind Screens in New Jersey, USA
Caithness Long Island LLC
Long Island experiences strong windy conditions and storms often coming in from the Atlantic Ocean. During these conditions the Energy Center experienced both thermal performance challenges as well as mechanical issues...
OPC Rotem Power Station in Dimona, Israel
OPC Rotem Combined Cycle Power Plant
OPC Rotem Combined Cycle Power Plant is a 440MW dual-fuel fired power project, located in Dimona, Southern Israel. Galebreaker and the OPC Rotem Engineering Team concluded that steam turbine output registered an average...
Preventing Fan Trips in Saskatchewan
Reducing dynamic fan blade loading at North Battleford Power...
Reducing Fan Stress in Nevada
Tackling fan performance issues at the Higgins Power Station Air...